BUS phase monitor for SIBELON systems for monitoring the normal mains supply
Each I-CONNECT 16 communicates with the SIBELON system via the BUS cable. A unique BUS address is assigned to each I-CONNECT 16 in the factory. A location text can be assigned at any time
(to enable accurately targeted correction of a local fault in the normal mains supply.
As soon as one of the normal mains supply phases to be monitored falls below the nominal voltage by more than 15 %, the BUS phase monitor signals a local mains failure. The LPS/CPS system now switches on the emergency lighting off the area concerned and supplies the luminaires via the mains.